Horizontal shading tools Depth = 0.25 Ground Floor First Floor
Good light distribution. Light level conforms with specifications. Working hours schedule General settings
Total heating load per meter =12.7 KWh total cooling load per meter =13.5 KWh Total heating and cooling load per meter = 26.2 KWh Low heating and cooling loads Energy conservation The recommended acceptable PMV range for thermal comfort from ASHRAE 55 is between -0.5
and +0.5 for an interior space. Comfort For library Comfort For classroom Hand calculation Lw = 75 db Back ground noise = 35 db
Standards Measured Empty Fully occupied RT60 :
0.6 - 0.8 s .7175 0.601 S/N : 10 - 30 dB
31.1 31.4 Ecotect calculation Ceramic Tiles
wall ( paint) Pageboard over 25mm(1") fiberglass board window(glass) The following results are
obtained from Ecotect software. Both hand calculation and software calculation are acceptable. Mechanical Design
Plumping system Drainage system. Water system. Firefighting system. Gas system. Plumbing Fixtures
Used plumbing fixtures in the project are: Water closets. Kitchen sinks. Lavatories (also called bathroom sinks). Drinking fountains. Drainage system :
The main pipes are U.P.V.C with 4size and P.V.C 2 size for internal connection and 6 U.P.V.C for outdoor pipes. All pipes (2,4 and 6 pipes) have slope equal to 1% to let the waste water flow by gravity. The manholes are connected with the vertical, the last manhole is connected with septic tank in the garden. The pipes size between the manholes is 6 to ensure good flow rate. water system :
The system is designed based on flush tank and public used for all fixture unit The cold and hot water are supplied to the fixture unit from the roof tanks and solar heater by the copper collectors and flow throw galvanized steel pipe and BEX pipe by gravity with different diameters and different lengths. The hot water is supplied to the building by solar heater in the summer and by electrical heater in the winter
Total cold fixture units: 168 fixture unit Total cold water flow rate that supply the building: 3.86 L/s Total hot fixture units: 42 fixture unit Total hot water flow rate that supply the building: 1.01 l/s A pump needs to supply hot water to first floor with head equal 38 kpa and Q equal 3.86 L/S
and its fixed on the return pipes to protect the pump from heat of water. A pump will be used to lift water to roof tanks from water tank when there is shortage in water in . the tanks and when the city water is cutoff The flow rate for the pump is set to be 10 M3 /HOUR with HEAD= 159 KPA The system designed according to the NFPA code and tables, in our project a fire cabinet is used in addition to the landing valves.
A single riser is used to feed the fire cabinets and landing with size equal 4 . Three pumps are used to run the system, the required flow rate for water from the pumps equal to 500 G.P.M according to the NFPA for 1 riser . Size of pipe which supply the fire
cabinet equal 1.5 and 2.5for landing valve The system is designed to supply 250 gpm for fire cabinets and 250 gpm for landing valve. The pump calculation is made for the landing valves in the first floor (the highest and the farthest point in
the building ) because it has higher flow pressure equal at least 100 psi. The pump flow rate (Q): 500 G.P.M. Pump head equal 128 psi or 840 Kpa. Jockey Pump. (P) HEAD jockey = 133 psi The pump flow rate (Q): 50
G.P.M. .Gas is needed to supply laboratorys, kitchens and canteens In general the gas supplier is gas cylinder which is located in suitable place in the school outside the .building . In this type of building (schools), the gas network has very low pressure and negligible friction losses .In this project the gas outlets equals 11 points .The GF has 2 gas cylinders which are used to supply the building 'The size of the pipes equal 0.5 for each gas outlet, and the main supply pipe size equal 3/4 Electrical Design
Sensor Protocols for Information via Negotiation, SPIN. A Negotiation-Based Protocols for spreading Information in Wireless Sensor Networks. Dissemination is the process of distributing individual sensor observations to the whole network, treating all sensors as sink nodes. Replicate complete view of...
Introduction To Robot Sensors. When - after students have learned about Boolean expressions and relational operators. Goal - students to develop a mental model of how robots make decisions . The lesson includes: an introduction to sensors
Title: A Decade of Research on Internet Enhanced Education Last modified by: kashy Document presentation format: On-screen Show Other titles: Times New Roman HG Mincho Light J Wingdings Small Fonts Arial CommonBullets Default Design A Decade of Research on Internet...
Orthogonal functions Fourier Series Discrete Fourier Series Fourier Transform: properties Chebyshev polynomials Convolution DFT and FFT Scope: Understanding where the Fourier Transform comes from. Moving from the continuous to the discrete world. The concepts are the basis for pseudospectral ...
Approximate computing. We're producing more data than we can analyze. Many applications do not require precise outputs. Being precise is expensive. Approximate computation. Time and/or energy vs. accuracy [IEEE Design 2014] Technology. scaling. Data warehouse growth. growth rate= 173%. TB
Group Synthesis. Well done. Each of you has not only gained the broad picture, but is also an expert in your role. You will need to get together as a team to share your different expert perspectives on the big...
(adjective) The rich and creamy chocolate melted in her mouth. (adjectival phrase) An adjectival phrase can give more detail about a noun. It can help to answer the questions: a) Which chocolate? b) What was the chocolate like? eg She...
cluster of water molecules. Net flow of water. Water. molecule. Equal. concentration. of solute. Higher. concentration. of solute. Figure 5.4 Osmosis, the diffusion of water across a membrane. Note that osmosis is a force that is actually able to cause...
Ready to download the document? Go ahead and hit continue!